Cooling Tower Terminology
A Cooling Tower is a heat rejection device that transfers heat from hot water into the atmosphere. In Cooling Tower Terminology the main objective of a cooling tower is to remove heat from water by evaporating a small portion of water and the treated water is then recycled back through the unit. When then warm water is mixed with cooler air, it releases latent heat of vaporization making the water cool and better for reuse in equipment. Cooling tower manufacturer(s) provide water treatment that is best for refrigeration systems and is commonly used in heavy industries like petrochemical plants, power plants, chemical processing, steel mills, and many more which mandate cooling as necessary.
A Cooling Tower Manufacturer also makes Cooling towers ideally to provide comfort cooling for large commercial buildings like airports, schools, hospitals and hotels. There are many buildings using a cooling tower in Delhi.
These towers have different mechanical processes that are identified by some unique scientific names. Let us go through the Cooling Tower Terminology:
Cooling Tower Terminology at a glance:
Approach: This is the most important measure of the difference between the temperature of the cold water that leaves the tower and the wet-bulb temperature of the air. Once the approach is measured, it determines the operating temperature of the tower and can also help in identifying an ideal tower size and cost.
Bleed Off: When dissolved solid concentrates collect in the water, that circulating water in the tower is discharged to waste because it helps to control the level of waste disposition below the allowable limit. This is an important factor to control solids concentration.
Biocide: Microbes can give foul smelling odor in the water. Biocide is a chemical agent used to treat and control the population of microbes by killing them.
Blowdown: The portion of water that is purposely discharged from the cooling system to control concentrations of impurities like salts, alkali and calcites in the circulating water. It is necessary to keep the water away from harmful solvents.
British Thermal Unit (BTU): It is the measurement of heat energy which raises the temperature of one pound of water one degree Fahrenheit in the range from 32° F to 212° F.
Cooling Range: This is the measure of temperature between the hot water that enters the tower and the treated cold water that exits it.
Cycles of Concentration: Dissolved solids in makeup water are compared with concentrated solids in the circulating water through evaporation.
Dissolved Solids: There are different solid mixes in water including both ionic and polar. Total solids that have been dissolved into a liquid are called dissolved solids.
Drift: When the water is exposed to air by pressure through the fan, it is discharged to the atmosphere. But drift loss is not the portion of water which is lost by evaporation. Proper tower design can minimize drift loss.
Heat Exchanger: is a device for transferring heat from one substance to another. Heat transfer can be by direct contact, as in a cooling tower, or indirect, as in a shell and tube condenser. Can also be the tube or fin tubed bundles in a wet/dry tower.
Heat Load: When the water is processed, it contains heat that is to be removed from the circulating water within the tower. Heat load equals water circulation rate (gpm) x cooling range x 500. It is expressed in BTU/hr. Both tower size and cost are determined by heat load.
Makeup: Additional water is added to fill the water loss due to causes like bleed off, drift, and evaporation. This additional water is called makeup water.
Pumping Head: A water ejection pump pulls up water from the tower basin to the top of the tower through its entire web. It is called a pumping head.
Ton: Water evaporation is measured by cooling ton that is 15,000 BTUs per hour.
Wet Bulb: This is the lowest temperature that water can reach by evaporation and is measured by psychrometer. It enables to select tower and design.
After this "Cooling Tower Terminology", if you require more information, you can meet a Cooling Tower manufacturer and also visit a Cooling tower in Delhi to gain more insight into how it works.
Why cooling towers are better than chiller
Chiller and cooling towers both are used to remove heat from a liquid used as a coolant in large ...
Why it is important to install a cooling tower
Cooling towers are a special heat exchanger in which air and water are brought i...
How to face common problems of cooling towers
For the cooling towersRead More
Five Steps to Maintain Cooling Towers
A Cooling Tower is specialized equipment used in industries aroun...
Facts about Cooling Tower Level Control - Kooldrop
Difference between cooling tower and condenser
A Cooling Tower is a heat exchanger ...
Are you confused among cooling tower Manufacturers? Here is the way out
The function of a Read More
Cooling Tower Material and its Main Components
Cooling Towers are an essential feature for many industries as it helps to reject excessive heat....
Cooling Tower Terminology
A Cooling Tower is a heat rejection device that transfers heat fr...
Difference between Natural Draft and Forced Draft Cooling Towers
Due to continuous mechanical processes, industrial processes and machinery generate huge amounts ...
10 Most important Characteristics of Cooling Tower Water Treatment
A cooling tower water system is the process of separating heat from hot water and then ejecting t...
Fundamental Principles of Cooling Towers
Cooling towers are heat exchanger units to expos...
How we choose best Cooling tower manufacturers
A Cooling Tower is the best mechanism to treat your equipment and save water. Pe...
Types of Wood used in Wooden Cooling Towers
Wooden cooling towers have been an old construction mechanism but over the period of time due to ...
Improving Energy Efficiency of Cooling Towers
Improving Energy Efficiency o...
Types of cooling towers
Understanding the Different Types of Cooli...
The Process of Cooling Tower Water Treatment System
Industrial companies often use a cooling tower to facilitate proper functioning ...
How Cooling Towers Work
A Cooling Tower is a heat exchanger device meant specifically for cooling down m...
What is the Purpose of fill in a Cooling Tower?
The Cooling Tower contains fills as the main com...
What is the difference between a Chiller and a Cooling Tower?
If you’re going to buy a cooling system for your company an...
Copyright © 2018 Kooldrop - All Rights Reserved.